piping questions and answers pdf free download
1. How can flanges be classified based on Pipe Attachment?
Flanges can be classified based on pipe attachment as: –
Slip – on. : – The Slip-on type flanges are attached by welding inside as well as outside. These flanges are of forged construction.
Socket Weld. : – The Socket Weld flanges are welded on one side only. These are used for small bore lines only.
Screwed. : – The Screwed-on flanges are used on pipelines where welding cannot be carried out.
Lap Joint. : – The Lap Joint flanges are used with stub ends. The stub ends are welded with pipes & flanges are kept loose over the same.
Welding Neck. : – The Welding neck flanges are attached by butt welding to the pipe. These are used mainly for critical services where the weld joints need radiographic inspection.
Blind. : – The Blind flanges are used to close the ends which need to be reopened.
Reducing. : – The reducing flanges are used to connect between larger and smaller sizes without using a reducer. In case of reducing flanges, the thickness of flange should be that of the higher diameter.
Integral. : – Integral flanges are those, which are cast along with the piping
component or equipment.
How can flanges be classified based on Pressure- temperature ratings?
Flanges are classified based on pressure temperature ratings as: –
Pressure temperature rating carts in the standard ASME16.5 specify the non-shock working
gauge pressure to which the flange can be subjected to at a particular temperature.
How can flanges be classified based on facing?
Flanges are classified based on facing as: –
- Flat face. (FF)
- Raised face. (R/F)
- Tongue and groove. (T/G)
- Male and female. (M/F)
- Ring type joint. (RTJ)
How can flanges be classified based on face finish?
Flanges are classified based on face finish as: –
- Smooth finish.
- Serrated finish.
Where the smooth finish flange & serrated finish flange finds its use?
The smooth finish flange is provided when metallic gasket is provided and serrated finish flange is provided when non-metallic gasket is provided.
What are the types of serrated finish provided on flange face?
- Concentric or
- Spiral (Phonographic)
How the serration on flanges is specified?
The serration on flanges is specified by the number, which is the Arithmetic Average Rough
Where the concentric serration is insisted for face finish?
Concentric serration are insisted for face finish where the fluid being carried has very low
density and can find leakage path through cavity.
How the Gaskets are classified based on the type of construction?
Based on the type of construction, gaskets are classified as: –
- Full face.
- Spiral wound metallic.
- Ring type.
- Metal jacketed.
- Inside bolt circle.
What is the most commonly used material for Gasket?
Compressed Asbestos Fibre.
Which type of gasket is recommended for high temperature & high-pressure application?
Spiral Wound Metallic Gasket.
What are the criteria for selection of MOC of Spiral Wound metallic Gasket winding material?
The selection of material of construction for Gasket winding depends upon: –
- The corrosive nature and concentration of fluid being carried.
- The operating temperature of the fluid.
- The relative cost of alternate winding material.
What are the most common materials used for spiral wound metallic gasket winding?
The most commonly used material for spiral wound metallic gasket winding is: –
- Austenitic stainless steel 304 with asbestos filler.
- Austenitic stainless steel 316 with asbestos filler.
- Austenitic stainless steel 321 with asbestos filler.
Which material is used as filler material for spiral wound gasket in case of high temperature services?
For very high temperature services, graphite filler is used.
What is centering ring in connection to spiral wound gasket?
Spiral wound gaskets are provided with carbon steel external ring called centering ring.
What will be the AARH finish on flange face for using spiral wound gasket?
125-250 AARH finish.
On which type of flanges the use of spiral wound gasket are restricted?
rating spiral wound gasket on flanges other#ASME B16.5 does not recommend the use of 150 than welding neck and lapped joint type.
Up to what temperature limits the low strength carbon steel bolts should not be used for flanged joints?
C.°C or below – 28°Flanged joints using low strength carbon steel shall not be used above 200
How the pipe fittings are classified based on end connections?
Pipe fittings are classified based on end connection as: –
- Socket weld fittings.
- Screwed end fittings.
- Beveled end or Butt weld fittings.
- Spigot socket fittings.
- Buttress end fittings.
Up to what temperature the carbon steel materials shall be used?
Carbon steel materials shall be used for temperature up to 425C°
Which material is used for temperature above 426C°?
Alloy steel materials shall be used for temperature above 426 C°
Which type of material is used for corrosive fluid?
Stainless steel materials shall be used for corrosive fluid.
Which type of piping materials are used for drinking water, instrument air etc?
Galvanized steel materials shall be used for drinking water, instrument air and NI lines (LP).
What is the difference between Pipe and Tube?
Pipe is identified by NB and thickness is defined by Schedule whereas Tube is identified by OD & its thickness as BWG (Brimingham wire gauge or 1/100 inch).
From which size onwards NB of pipe is equal to OD of Pipe?
From the size 14” and onwards NB = OD of pipe.
What should be the radius of long radius elbow?
1.5D (Where “D” is the diameter of the pipe.)
What should be the radius of short radius elbow?
1D(Where “D” is the diameter of the pipe.)
What is the basis of using of short radius & long radius elbow?
Long radius elbow are used for small pressure drop whereas short radius elbow are used for high pressure drops. For catalyst flows vary long radius elbows are used.
Normally where do we use the following?
(1) Eccentric reducers. (2) Concentric reducers.
- Eccentric reducers = Pump suction to avoid Cavitation, To maintain elevation (BOP) in rack.
- Concentric reducers = Pump discharge, vertical pipeline etc.
Concentric reducer is used in pump suction. (Yes / No). Explain.
No. Air pockets may form if concentric reducer is used at pump suction, which results in cavitation
and cause damage to Pump. To avoid this problem, Eccentric Reducer with flat side up (FSU) is
used in Pump Suction.
Where the ERW spiral & longitudinal pipes are used?
Use depends upon the availability of pipes. Nothing functional difference.
Where the ERW & Seamless pipes are used?
Above 18” ERW pipes are used. Below 18” seamless pipes are used. Seamless pipes can sustain
higher temperature & pressure.
What is the main use of ASTM A53 & A106 Gr.B pipes?
ASTM A53 pipes are mainly used for utility services whereas A106 Gr. B pipes are used for high
Pressure & high temperature services.
From which side of pipe will you take a branch connection?
When fluid is Gas, Air or Steam and Cryogenic Service – Topside.
When Fluid is Liquid – Bottom Side.
Why don’t we take a branch for Cryogenic Service from bottom side though the fluid is in liquid state?
There is the chance of ice formation during normal operation and since ice flows from the bottom of the pipe it will block the branch pipe connection.
Why do we provide High Point Vent (HPV) and Low Point Drain (LPD) in piping?
HPV – For removing Air during Hydro-test.
LPD – For draining water after conducting Hydro-test.
What do you mean by Jacketed Piping?
Piping which is recognized as providing the most uniform application of heat to the process, as well
as maintaining the most uniform processing temperatures where steam tracing is not capable of
maintaining the temperature of fluid constant. Usually used for molten sulphur, Polymers service.
What is the minimum distance to be maintained between two welds in a pipe?
The thumb rule is that the minimum distance between adjacent butt welds is 1D. If not, it is never
closer than 1-1/2″. This is supposedly to prevent the overlap of HAZs. Minimum spacing of
circumferential welds between centerlines shall not be less than 4 times the pipe wall thickness or
25 mm whichever is greater.
What do you mean by IBR and which lines comes under IBR purview?
IBR: Indian Boiler Regulation Act.
Steam lines with conditions listed bellow comes under IBR purview : –
- Lines for which design pressure is 3.5 kg/sq. cm and above.
- Line size above 10” having design pressure 1.0 kg/sq. cm and above.
- Boiler feed water lines to steam generator, condensate lines to steam generator and flash drum.
What are Weldolet and Sockolet? And where they are used?
Weldolet and Sockolet are basically self-reinforced fittings.
Weldolet is used for Butt weld branch connection where standard tee is not available due to size
restrictions and the piping is of critical / high-pressure service. Sockolet is used for socket welding
branch connection, which require reinforcing pad.
What is the MOC for Superheated high pressure Steam Lines?
A 335 Gr. P I / P 11, Composition: Cr. – ½ Mo (P1) / 1¼ Cr. – ½ Mo (P11)
What is the normal upstream and downstream straight length of orifice flow meter?
Upstream – 15D Downstream – 5D
This entry was posted in Interview Questions and Answers, Piping Interview Questions Answers and tagged 22 Pipefitter Interview Questions and 132 Answers, most commonly asked questions in piping interview, pipe fitter interview questions and answers, pipe fitter interview questions pdf, Pipe Fittings Frequently Asked Questions, Pipe Fittings- FAQ, pipefitter questions answers, piping interview question and answer pdf, piping questions and answers pdf, piping questions and answers pdf free download, piping supervisor interview questions and answers, Question and Answers on Piping related topics, Questions about piping issues, Questions Related to Pipe Fittings, SAMPLE TEST QUESTIONS STEAMFITTER/PIPEFITTER, Searches related to Questions related to Pipe Fittings, Top 10 piping interview questions with answers.
Questions Answers Related to Codes & standard: –
1. Q:-What is the ASME code followed for design of piping systems in Process piping (Refineries
& Chemical Industries)?
(i) B 31.1
(ii) B 31.3
(iii) B 31.5
(iv) B 31.9
2. Q:-Which American institute standard does piping engineer refer?
A. The American Petroleum institute (API).
B. The American Iron & Steel institute (AISI).
C. The American Society for Testing and materials (ASTM).
D. The American National standard institute (AISI).
E. The American welding society (AWS).
F. The American Water Works Association (AWWA).
G. The American Society for Mechanical Engineers (ASME).
3. Q:-What is the different ASME 31 code for pressure piping?
A. ASME B31.1 – Power piping.
B. ASME B31.2 – Fuel Gas Piping.
C. ASME B31.3 – Process piping.
D. ASME B31.4 – Pipeline Transportation system for liquid hydrocarbon & other liquid.
E. ASME B31.5 – Refrigeration Piping.
F. ASME B31.8 – Gas transmission & distribution piping system.
G. ASME B31.9 – Building services piping.
H. ASME B31.11 – Slurry transportation piping system.
4. Q:-What are the different sections of ASME code? Where these sections are referred?
A. ASME section I : – Rules for construction of power boiler.
B. ASME Section II : – Materials.
Part A – Ferrous materials.
Part B – Non-Ferrous materials.
Part C – Specification for electrodes & filler wire.
Part D – Properties.
C. ASME Section IV : – Rules for construction of Heating Boiler.
D. ASME Section V : – Non- destructive Examination.
E. ASME Section VI : – Recommended rules for care & operation of heating boiler.
F. ASME Section VII : – Recommended guidelines for care of power boiler.
H. ASME Section VIII : – Rules for construction of pressure vessels. (Division I & II)
I. ASME Section IX : – Welding & Brazing qualification.
5. Q:-Which American standard is reffered for selection of following piping element?
A. Flanges B. Butt Welded fittings C. Gasket D. Socket & Threaded fittings
E. Valves F. Pipes.
A. Flanges :-
I. ASME B16.1 : – Cast iron pipes flanges & flanged fittings.
II. ASME B16.5 : – Carbon steel pipes flanges & flanged fittings. (Up to 24”)
III. ASME B16.47 : – Large Diameter steel flanges. (Above 24”)
B. Butt welded fittings :-
I. ASME B16.9 : – Steel butt welding fittings.
II. ASME B16.28 : – Butt-welded short radius elbows & returns bends.
C. Gasket :-
I. ASME B16.20 / API -601: – Metallic gaskets for pipe flanges- Spiral wound,
Octagonal ring Joint & Jacketed flanges.
II. ASME B16.21 : – Non metallic gasket.
D. Socket & Threaded fittings :
I. ASME B16.11 : – Forged steel socket welding & threaded fittings.
E. Valves :-
I. ASME B16.10 : – Face to face & end to end dimension of valves.
II. ASME B16.34 : – Flanged & butt-welded ends steel valves (Pressure &Temperature ratings)
except Ball, Plug & Butter fly Valves.
F. Pipes :-
I. ASME B36.10 : – Welded & Seamless wrought iron pipes.
II. ASME B36.19 : – Stainless steel pipes.
If you are Interested to attend our AWS CWI Seminar, Please Fill the Enquiry Form:
This entry was posted in Piping Interview Questions Answers and tagged 11 most important questions & answers from ASME B, interview questions on piping projects, pdms piping designer interview questions, Piping Design Engineer Interview Questions, piping design interview questions and answers pdf, Piping interview questions, PIPING INTERVIEW QUESTIONS PART 1, piping questionnaire pdf, piping questions and answers pdf free download, piping related question and answer, piping supervisor interview questions and answers, Searches related to Piping Interview Questions Answers Related to Codes & standard, sp3d piping interview questions, Top 10 piping interview questions with answers.